Talking about the Low Pressure of the Condensation Failure of the Water Chiller
The low condensing pressure of the condenser is often caused by insufficient refrigerant, because it is not very common that the condenser has a low pressure. The condensing pressure of the condenser tends to be high. If the condensing pressure of the condenser is low, first It should be checked whether the refrigerant is sufficient.
In other words, first check whether the refrigerant is missing. If there is a lack of refrigerant, low condensing pressure is an inevitable situation, and low condensing pressure is not necessarily caused by the lack of refrigerant.
Low condensing pressure may also be caused by the damage of the condenser itself. Condensers are divided into water-cooled and air-cooled condensers. Different condensers have different working principles and different design and manufacturing concepts. If the condenser itself is damaged, it will be easy to cause the condenser. The condensing pressure is too low.
Second, the solution.
The condensation pressure of the condenser is low. If it is caused by the lack of refrigerant in the chiller, it is recommended to fill the chiller with sufficient refrigerant. After the yong point, take measures to compensate for the leakage, and then add sufficient refrigerant, the problem can be solved.
If the condensation pressure of the condenser is low due to the damage of the condenser itself, it is recommended to ask professionals to inspect, repair and replace, especially during the warranty period, please do not repair without authorization to avoid the manufacturer’s rejection of the warranty.