Emergency treatment method for water shutdown of induction melting furnace water system
A. Induction melting furnace water system shuts down
The first step is to start the generator, if the start fails, then the emergency water is turned on
The second step is to check the water pressure of the emergency pump. Close the valves at the inlet and outlet of the furnace body.
The third step is to check the furnace body return water pipe, the water temperature is too high, the return water temperature, open the furnace body emergency, check the emergency water, the water outlet, Check whether there is water flowing out of the water inlet and outlet valves, check the furnace body’s return pipe and the temperature of the return water.
B. Precautions after the emergency water start of the induction melting furnace
1. The first time to observe whether there is water flowing out of the emergency water outlet. If there is no water flowing out of the water outlet, it means the water circulation pipe
There is no emergency water replenishment in the road or the valve on the relevant pipeline is not opened. It is necessary to find out the reason immediately and replenish the emergency water in time.
2. In the emergency water working state, the on-site personnel need to detect the temperature of each furnace body’s return water pipeline at all times. If the temperature of each pipeline is found
When it continues to rise and there is no cooling trend, the molten iron in the furnace should be poured out in time.